New DEC museum entry :D
ard at p850ug1.demon.co.uk
Wed Feb 21 18:39:55 CST 2007
> On 21/2/07 06:11, "Bob Bradlee" <caveguy at sbcglobal.net> wrote:
> > would heat up and pop, I swaped the breaker out with a different one of the
> > same size and it that held just
> > fine. The circuit I moved the week breaker to, normally only runs 7 or 8 amps
> > and it never failed with the
> > light load.
> Thing is, if it was something like that then the 32A breaker running the
> upstairs ring main would pop rather than the whole house, that to me shows
> more of a sudden leak to earth than anything else. It's still odd that the
> Pro's own PSU breaker doesn't pop before anything else does.
That 32A MCB and the breaker in the Pro are current-operated devices.
I'll bet the main switch is an RCD (and not current operated at all), and
what's tripping the latter is an earth leakage problem.
Thing is, some older mains filters have a fairly high earth current
anyway (one reason I don't want an RCD anywhere near the mains to my
workbench). SO there may not be an actual fault. But replaceing the
filter (or the capacitors, possibly with lower value ones) might get it
The 5 minute delay is a puzzler though...
More information about the cctech